An equipment malfunction at a substation forced the shutdown of Columbia Generating Station.
Washington’s lone nuclear plant reconnected to the Northwest power grid late Saturday, six days after an equipment malfunction caused an unplanned shutdown.
Energy Northwest said operators of the Columbia Generating Station, near Richland, have been slowly raising power levels and expect to reach 100 percent within 72 hours of restarting.
The plant shut down at 11:24 p.m. Dec. 18 after a malfunction at the Bonneville Power Administration’s nearby Ashe Substation. The substation handles all the electricity produced at the Richland plant.
The malfunction caused the 500-kilovolt line that connects the plant’s main output transformers to the substation to reject the load. A primary breaker that was supposed to open was slow to do so, but a secondary system kicked in and opened other breakers, causing the plant to separate itself from the grid and shut down.
Most Read Stories
- Give to panhandlers or don’t? Some towns try cracking down
- Ex-Seahawk Marshawn Lynch watches Raiders game from the stands, rides BART train after being ejected
- Seattle startup co-founder Matt Bencke was ‘a force of nature’ | Obituary
- A chilly La Niña winter likely in Pacific Northwest, but don’t fret about drenching of last year
- Check out this new drone footage of the Bertha-dug Highway 99 tunnel WATCH
Columbia Generating Station is the third-largest power plant in the state. It sends enough power to the Northwest grid to power a city the size of Seattle.